Reinstall the access panel and disconnect block. Turn on the circuit breaker and furnace switch. Then set the thermostat to a lower temperature and wait for the AC to start (see “Be Patient at Startup,” below). The compressor should run and the condenser fan should spin. If the compressor starts but the fan doesn’t, the fan motor is most likely shot. Shut off the power and remove the screws around the condenser cover. Lift the cover and remove the fan blade and motor (photo 7). Reinstall the blade and secure the cover. Then repower the unit and see if the fan starts. If it doesn’t, you’ve given it your best shot—it’s time to call a pro.
Cleaning the debris that builds up on your filters will aid with the flow of air. When your air filter is clogged, your air handler must work harder to compensate for the blockage of air flow. In addition to driving up your utility bill, the reduced air flow through your heating and cooling system can cause your heat exchanger to overheat and shut off too quickly.