For residential homes, some countries set minimum requirements for energy efficiency. In the United States, the efficiency of air conditioners is often (but not always) rated by the seasonal energy efficiency ratio (SEER). The higher the SEER rating, the more energy efficient is the air conditioner. The SEER rating is the BTU of cooling output during its normal annual usage divided by the total electric energy input in watt hours (W·h) during the same period.
Your furnace's flame sensor is essentially a safety mechanism. As a thin metallic rod in front of the flame inside the unit, it's sole purpose is to confirm that your gas valves only open when a flame actually exists to burn that gas. When the flame sensor stop working, on the other hand, gas leaks can occur. To repair your furnace's flame sensor, expect to spend between $80 and $250. Even a full replacement of this part typically does not go above that range.
A contactor is a $25 mechanical relay that uses low-voltage power from the thermostat to switch 220-volt high-amperage current to the compressor and condenser fan. AC contactors can wear out and are at the top of the list of common air conditioning service failures. Even if your contactor is working, it pays to replace it every five years or so. Unscrew the old contactor before removing the wires. Then move the wires to the new unit (photo 6).
If you hear clicking that is followed by a hum or buzz, you’re probably hearing the fan motor attempting to start without the boost it needs from the capacitor. You can almost always conclude that the capacitor has failed. Sometimes you can get the compressor fan spinning (clockwise) by pushing it with a thin stick or long screwdriver poked through the grille. But the chances are good that this might work for one cycle, but the capacitor will fail next time the AC goes on. It’s best to replace the capacitor.
Cleaning the debris that builds up on your filters will aid with the flow of air. When your air filter is clogged, your air handler must work harder to compensate for the blockage of air flow. In addition to driving up your utility bill, the reduced air flow through your heating and cooling system can cause your heat exchanger to overheat and shut off too quickly.